Thermodul is approved to EN442-1 and -2 for water based heating systems and meets the requirements of the 89/106/EEC directive.
|Materials||Furnishing element in aluminium, heating core with supply and return copper piping external diameter 14.7 mm. thickness 0.6 mm, heating fins aluminium|
|Dimensions||Height 137mm, width 29mm|
|Water capacity||0.29 litres/metre|
|ΔT=50K (tested to EN442-1 & EN442-2 at Politecnico di Milano)||Thermal output of the tested model: 146.4W/metre|
|Maximum length per single circuit||20 m. Beyond 20m it is important to evaluate the pressure head loss and return temperature.|
Water Version Heat Output
The table below shows the thermal emission per linear meter with respect to the variation of the difference in temperature between the water and the air. For a standard condensing boiler we recommend using ΔT 50°C.
|Output Power in Watt/metre||75.5||92.2||109.7||127.7||146.4||165.7||185.5|
|Output in Btu/hr/metre||258||315||374||436||500||565||633|
Tests at the Politecnico di Milano show just how evenly Thermodul distributes heat around a room.
Download water version installation instructions (1.25MB PDF)
The electrical version of Thermodul Skirting Heating meets the requirements of the 89/106/EEC directive.
The electrical version outputs 200w per metre.
Heating elements are composed of aluminium containing various powered armoured resistors depending on length.
Electrical connection example: